for Worthington, OH
Wonderful, professional service.
Suzanne - Worthington, OH
David - Worthington, OH
Dennis - Worthington, OH
Pickerington Heating and Cooling returned for a furnace tune up. They called ahead, arrived on-time and performed the tune up as promised. A capacitor needed to be replaced.
Thorough personal service.
CG - Worthington, OH
Performed a diagnostic service call for ( our ) AC unit. Filter dirty. Found capacitor bad, replaced. Found unit low, re-charged. System has a leak, need to return for leak search and warranty repair.
Upon arrival I gave the customer an Estimate on Full System.
Performed a sma tune-up and safety check-up for a 2017 AC unit. Completed full service AC tuneup and found no issue with the equipment, components or refrigerant charge. This system is operating properly at this time and was left operable upon my departure.
Performed a diagnostic service call for a 2008 gas furnace. Found thermostat blank. Power switch to furnace turned off, replaced filter with customer’s own, turned switch on. Cycled heat, all operating well at this time. Furnace is pretty new, A/c is newer. All good at this time.
Upon arrival I completed the Scheduled Maintenance Agreement Tune-Up. I visually inspected the unit. I checked the voltage, amps and pressures. I completed the combustion analysis. I cycled and monitored the system. The system is operating normally at this time.