for Granville, OH
I completed Full Install Carrier 96% Two-Stage 80,000 BTU Gas Furnace. Carrier 16 SEER 3.5 Ton Heat Pump; The system is operational upon departure.
After removing the Lennox Electric furnace and Lennox heat pump, I installed a Carrier Multi-Speed X-13 3 Ton Electric Furnace / Slant and a Carrier 14 SEER 3 Ton Heat Pump. Cycled and monitored the system. Operating normally at this time. Included with the installation is a free 1 year service maintenance agreement.
Installed honeywell smart home thermostat. Has 6 wires R-C-W-W2-Y-G normally wired. Programmed equipment. Helped customer set wifi, in order to add app he has to register it, had him take a picture of the registration information displayed. He will take care of this and set his personal schedule. Cycled heat, fully operational. Cycled AC fully operational.
customer explained that after he made the phone call for the appointment he checked the filter. Was quiet a bit passed needing changed. Let it melt all night and tried again no ice on system. Going to check temp drop on system and if it is correct going to move through a full time up on system. Brand new hyper allergenic filter these filters are thicker than other so even a couple months of dust can restrict airflow to the point of ice. Temp drop 70.2 in 49.9 out. Temp drop is very good. Going to do full tune up on system.
Tuneup and safety check on Concord AC for Granville customer. Unit is cooling properly at this time.