for Delaware, OH
Very Professional and Knowledgeable
Weidman - Delaware, OH
Service Technician called to let me know when he was arriving. He put on protective booties and proceeded to check Heating system. He stated that the system is a MERV 10 and the filter that is being used is a MERV 14 which overtime can damage the system. He recommended to use the Nordic Pure filter either MERV 6 or 8 it is not paper it has fibers which catches more dirt and can be bought on Amazon.
Parbin - Delaware, OH
Jake from Pickeringten provided awesome service and great suggestions to increase the performance of AC unit and clean house. Thank You.
Very thorough and courteous
Gary - Delaware, OH
Found filter dirty. Found standing water in furnace. Found heavy corrosion on heat exchanger and burner. Delta t is 55 degrees. Found water on board. Water damage on gas piping, gas valve, and inducer motor. Combustion analysis results are 9%o2, 115 ppm of co(within specs) System operational on departure.