for Whitehall, OH
Arrived on site customer has flood has not tried it too much. 120v to transformer 27 out to the board. The board is failing to send this low voltage out on the thermostat wires and led is failing to light up. The fuse is in tact checked continuity. Board has failed from the floods and needs to be replaced. 2002 Goodman System has water up above the blower motor more than likely it will need replaced going to order both and bring both out to save a trip if we need the blower motor.