for Gahanna, OH
Trumble - Gahanna, OH
I Replaced the Compressor-Motor Surge Capacitor on a Air Conditioner
customer says it runs you can feel cooler air just not cold. Put gauges on system pressure 96/264 53 degree super heat 4.1 Subcool. System is not fully charged from winter install. Checked for ice on evap coil in attic none no frost. Added 410a until Subcool is at labeled 10degrees. System took. 1lbs 6.25 ounces. Subcool now 9.9. Super heat 16 system is set to cool full of refrigerant and ready for operation.
Following COVID-19 Protocol, wearing mask and gloves and keep activity in the home to a minimum, I Performed A/C tune-up on a 2003 Goodman Air Conditioner . System is now running a peak performance.