for Powell, OH
Michael - Powell, OH
Austin was polite, professional and very knowledgeable. He explained the step by step procedures during furnace tune up. We are very comfortable knowing Austin provided services.
Knowledgeable Technician, overall great experience.
Ben - Powell, OH
Matt was very knowledgeable Technician and explained everything as he was checking the A/C unit. He was able to track down the problem and made a number of calls to understand my options for correcting. Matt seemed sincere in helping make it the best experience he could. Overall it was a very good experience.
Donna - Powell, OH
David - Powell, OH
The furnace was not working. Matt traced the electric power thru the system and documented where it Failed and quoted me on the repair. I am deciding wetner to replace the furnace or repair it.
Al - Powell, OH
The check of the AC unit went fine. It appeared to be thorough and was done on time and as expected. My only problems were the thermostat was not turned back on to heat (it’s a cold Spring) and the door to the furnace room was left open.
Superior service and advice
Michael - Powell, OH
Carl arrived on time, explained the service to be performed and was very helpful with thermostat programming. Carl also informed me of service results.
Rachel - Powell, OH
Great and prompt service, and very friendly!
Christi - Powell, OH
I called on a Friday for non-emergency service and had an appointment for Monday. I know at some point I will probably need to replace my old furnace, but until then, I will trust Pick Heating & Cooling to take care of it.
I completed scheduled maintenance spring tune up on a Carrier heat pump. I visually inspected the furnace. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked voltage and amps. Inspected heat pump. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
I completed a diagnostic on a Bryant Air Conditioner. I inspected the unit and found capacitor had failed. The outdoor coil is dirty but there is no access to water so I advised homeowner that cleaning that would help. I replaced capacitor and the system came on. Cycled and monitored system. Operating normally at this time.
Upon arrival System had water on floor around furnace. Inspected drain pain and it was clogged up. Cleaned drain. Ran system. System working properly at this time
I completed a diagnostic on an A/C. I installed delay on make timer. I cycled and monitored the system. Operating normally at this time.