for Powell, OH
Sudhir - Powell, OH
FU - Powell, OH
Professional and reasonable price
I found the heat pump off due to open low pressure switch. Heat pump has oil all over the internal parts looks like something blew inside causing all the refrigerant to leak out. I advised the customer we could either test the line for leaks and repair, or replace the system. The customer does not want to do anything at this time. System is not operational upon departure due to issues stated above.
Outdoor fan motor hasn't worked for about 3 days. Outdoor capacitor blown. Replaced capacitor with clients permission. Fan motor currently on but pulling .72A rated for .74A so the motor has sustained some damage from over heating for 3 days. Fan motor will fail soon. Client wants to wait. System operational upon departure, but could fail soon.
I performed a diagnostic on a Bryant 90% gas furnace due to unit stopped heating and no airflow. I found furnace coding 13 open limit. Furnace only has 2 limits and they are both closed and working within specs. Reset system about 3 times to get it to fire up. Heat came on without any issues. Blower Capacitor needs replaced. Inducer motor starting to grind and needs replaced. Circuit board possibly has an issue reading that the limits are closed. I explained options to the customer: Replace parts Replace furnace or whole system Due to age I recommended replacing the system vs wasting money on the old system. Client wants to wait for system to fail before replacing.