for Powell, OH
Service was thorough and excellent
Kevin - Powell, OH
Sudhir - Powell, OH
FU - Powell, OH
Professional and reasonable price
I completed the diagnostics and found the filter 100% blocked, The customer does not have one but he will go get one soon. The condenser coil 100% blocked. I cleaned it with water and informed the customer how important airflow is. There is no current issue after clearing airflow I “assume” system either froze or the condenser high pressure switch opened to prevent further issues I suggested regular maintenance. I also suggested to prepare to replace the furnace
I completed diagnostics and found the system completely empty on 410A. I explained to the customer their options of replace / repair. I also explained refill/easy seal with no warranty. I located leak and fixed it. The client doesn’t wanna move forward with anything at this time.
I completed the diagnostic checklist and found everything within manufactures specifications. No issues found. The system is operational upon departure.
I completed the diagnostics and found that the outdoor unit isn't making a noise at this time. The compressor sounds like it has a hard time on start up and the fan motor bearings are going out. I explained the options of replace / repair. the client isn't ready to move forward with options at this time.
I replaced the pan and ordered an evaporator coil. The system is operational upon departure.
I completed AC Spring Tune-Up and Safety Check on 2011 York. We need to perform leak search to determine location of leak and if it is repairable or not.