for Powell, OH
Michael - Powell, OH
Austin was polite, professional and very knowledgeable. He explained the step by step procedures during furnace tune up. We are very comfortable knowing Austin provided services.
Knowledgeable Technician, overall great experience.
Ben - Powell, OH
Matt was very knowledgeable Technician and explained everything as he was checking the A/C unit. He was able to track down the problem and made a number of calls to understand my options for correcting. Matt seemed sincere in helping make it the best experience he could. Overall it was a very good experience.
Donna - Powell, OH
David - Powell, OH
The furnace was not working. Matt traced the electric power thru the system and documented where it Failed and quoted me on the repair. I am deciding wetner to replace the furnace or repair it.
Al - Powell, OH
The check of the AC unit went fine. It appeared to be thorough and was done on time and as expected. My only problems were the thermostat was not turned back on to heat (it’s a cold Spring) and the door to the furnace room was left open.
Superior service and advice
Michael - Powell, OH
Carl arrived on time, explained the service to be performed and was very helpful with thermostat programming. Carl also informed me of service results.
Rachel - Powell, OH
Great and prompt service, and very friendly!
Christi - Powell, OH
I called on a Friday for non-emergency service and had an appointment for Monday. I know at some point I will probably need to replace my old furnace, but until then, I will trust Pick Heating & Cooling to take care of it.
Upon arrival I replace the Spacegard Air Cleaner Media 213. The system is operational at departure.
I completed the scheduled maintenance agreement fall tune up on a Carrier Infinity Series gas furnace. I visually inspected the unit. Checked voltages, amps and pressures. Completed combustion analysis. Cycled and monitored system. Operating normally at this time.
I performed a service call. Upon arrival customer stated that there is water leaking out of the bottom of the furnace. I found water was leaking out of the vent pipe where it comes out of the side of the furnace. I extended the vent pipe outside of the furnace and connected into the existing vent PVC pipe. Furnace is no longer leaking.
I arrived on site to perform an inspection of a Carrier air conditioning unit. During the inspection I found that the unit's capacitor had worn out, causing it to provide energy to the unit. I replaced the capacitor and the unit was running at full functionality at the time of departure.
I arrived on site to perform an inspection of the customers air conditioning unit. During the inspection I found that the unit's capacitor had blown out, resulting it it not working correctly. I replaced the capacitor and the unit was running at full functionality at the time of departure.
I delivered a portable AC to a client for temporary cooling.