for Dublin, OH
Excellent AC Tune Up
Ann - Dublin, OH
Hilliard-Dublin Heating & Air provided a very quick appointment as I scheduled my AC tune up. Matt, the tech was very professional, knowledgeable and thorough. I appreciated that the service cost was very reasonable (There was a "special" going on at the time I booked my service.) The tech called me about 30 minutes before his arrival to alert me to the time he would arrive. He donned booties so that his shoes would not soil my carpeting. He not only checked and serviced my AC very thoroughly but he also replaced my air cleaner filter with one he had on the truck. I immediately received an invoice via e mail and it listed all the items he checked and the results of his service check. I recommend this company very highly and also scheduled another service call for a second property I own.
Fantastic response on a Saturday; Professional & Knowledgable Service
Tom - Dublin, OH
I called on a Saturday morning with an A/C not working in July. By 1:15 pm it was fixed and cooling the house. I couldn't ask for a quicker response but also i was impressed by the professionalism of the technician and staff at Hilliard-Dublin Heating & Air. I highly recommend them.
Consistently great service!
Stephanie - Dublin, OH
Stephen - Dublin, OH
Fast trouble shooting. Outdated furnace to be replaced. Priced just right.
Terry - Dublin, OH
The technician “Matt” was experienced and honest.
Great service at a reasonable price
Mukesh - Dublin, OH
very nice associates and the job was very professionally done
Great service check up
John - Dublin, OH
Semi annual check up, very thorough. Went outside and pug gravel under ny unit to level it.
Amanda - Dublin, OH
Honest opinion. Quick service
KP - Dublin, OH
This was our first time using this company and we were very pleased with the technician's thoroughness. He also gave us some very helpful tips about our unit.
Brad - Dublin, OH
Technician came out to look at a loud HVAC system. Very friendly and helpful.
I added 2 pounds of Refrigerant R-410A Puron in to the Air conditioner
Inspected the 2005 lennox system, found everything in working order including refrigerant charge. Only issues found were the amp draw on the compressor. Compressor may fail soon and possibly has over heated from the high amp draw causing a no cooling message on the Ecobee.
Client stated the ac is working fine and keeps up on temp. He was just wondering if its okay for it to run a lot on a 90+Day. Checked refrigerant charge,R22 piston system. System is old but working within specs.
Outdoor capacitor blown. Replaced capacitor to find the thermostat not calling for cooling. Thermostat was wired incorrectly and has been damaged due to wiring. Replaced thermostat to find the system low on refrigerant 410A, has a leak.