for New Albany, OH
Arrived on site of the 2004 Bryant system was icing over they’ve had it off for three days. Cycled on temp drop is 10 degrees no ice on coil filter is brand new. Outside gauged up system is 44/220 r22 superheat is 58 should be 21-24. System is low on refrigerant which means we have a leak somewhere on the system
System has been moved off its pad and is pressed up against the house can see area where the metal guard is bent indicating this has been hit. Customer uses lawn care service and I had customer come outside, he confirmed this is a newer finding, and that the system was nice and level on that pad not pressed up against the house. When we move a system dramatically like this it stresses the copper fittings and can cause a leak like we are finding.
Customer is having issue with compressor on the 2013 ICP Heat Pump system has tried a hard start it split the hard start. I tried wiring up a 5-2-1 heavy hard start with potential relay and the compressor came on and we could hear it slow down slow down and seize. Compressor is seized at this point and needs to be replaced