for Groveport, OH
Great service, good prices awesome staff
anna brown - Groveport, OH
Diagnostic Service Call on 7 year old Bryant unit. Blower motor does not come on. Cabinet is rusty and is damaged from water Drain line is clogged and slopped incorrectly, causing pan to overfill and leak onto motor Hooked up motor from truck and it started. Ordered blower motor and will schedule as soon as possible
Maintenance has changed the coil already, but still leaking 410A. Advised maintenance that management would need to approve the leak test. Leak can also possibly be in the ground where the line set runs. Have to test the new coil and condenser.
Water all over the basement. Found no water in the pan. Filled it up cut and turned drain so it couldn’t drain out line to test for any cracks. Pan holds water not leaking. Found black T joint not glued. Seems to be right in the center of all the water. Glued it up sealed the duct work back up and system is operational.
Annual A/C maintenance checked performed on a Carrier unit. System readings and measurements found within manufacturer specifications.