for Blacklick, OH
I delivered portable heaters to the customer as they had to wait a day or two until their new system could be installed.
I found the system is lacking air flow and provided the customer with some options of what they could do as well as changes we could make to the system. I also provided a quote for an I wave air purifier after the customer asked for one. System is operational upon departure.
I found the system was lacking proper air flow and the filter size the customer installs needs to increase. I provided a quote per customer's request of an I wave air purifier, proper filters, and labor. Customer will contact us when ready. System is operational upon departure.
I performed a diagnostic on a Lennox 80% gas furnace. I found the inducer motor humming. I tried spinning the motor with my hands and it would start. Tested voltage coming to the motor 120v correctly. Re wired cycled on tried to spin it and it ran for a couple mins but wouldn’t make enough pressure to close switch. The motor has failed mechanically at this time and needs to be replaced.