for Hilliard, OH
Aimie - Hilliard, OH
We recommend you to everyone.
Jaime - Hilliard, OH
Fred - Hilliard, OH
Chris was thorough. It was a late night and he took the time to troubleshoot and find the issue.
We received top care and advice and a discount for the next time.
Wendy - Hilliard, OH
My family received top care.
Great service by one of your technicians
Randy - Hilliard, OH
Your technician was helpful, courteous, knowledgable and quick to solve the issue.
Response from Five Star Heating & Cooling Group:
Randy, Thank you for taking the time to review our company. We are so thrilled to hear you had a 5-star experience.
Tracey - Hilliard, OH
Fast service, and honest. Tech Chris was so professional.
tech was kind and informative
Kathleen - Hilliard, OH
Swain - Hilliard, OH
There wasn’t much he could do, the issue is still ongoing. But, he did all he could as the issue wasn’t currently on going when he got there
Outstanding Inspection Knowledge
Jeff - Hilliard, OH
We hired Pickerington Heating & Cooling to inspection a home air conditioning system in a house that we are considering to purchase. The individual that Pickerington sent to do the inspection was outstanding. He was very knowledgeable and confirmed our suspicions that the system was not working properly. He was able to identify the problem and present us with different options for fixing the AC. He walked us through every aspect of his inspection, gave us all of the options, and did not do any 'higher pressure' sales pitch to us. His inspection provided us the information we need to discussion remediation solutions with the seller. Thank you Pickerington.
Hennon - Hilliard, OH
Best experience with heating and and air provider ever
I completed the spring tune up on an air conditioner. I visually inspected the furnace. Checked voltage and amps. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
Performed a diagnostic on AC not working properly found unit to have a bad dual capacitor on outdoor unit recommended replacement of the 40/5 dual capacitor client accepted installed new dual cap unit is now working properly at this time
I completed a diagnostic on an A/C blowing warm air. I inspected the unit and found the filter is dirty. Customer replaced it. I found a bad capacitor as compressor would not start. I replaced capacitor. I cycled and monitored the system. Operating normally at this time.
I completed scheduled maintenance spring tune up on a Carrier heat pump. I visually inspected the furnace. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked voltage and amps. Inspected heat pump. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. I found the capacitor out of specs so I replaced that under warranty. Cycled and monitored the system. Operating normally at this time.
Client requested an estimate to replace a Bryant Air Conditioner. I recommended a Five Star 13 SEER 2.5 Ton Air Conditioner.
I completed a diagnostic on a Bryant A/C. I inspected the unit and found the charge off. I also found the fan speed was not correct. Corrected fan speed and charged system. Operating normally at this time.