for Pataskala, OH
Rachel - Pataskala, OH
Always easy to have our equipment services in the spring and fall.
Linda - Pataskala, OH
Adam was very patient and polite. Our two noisy dogs didn't faze him a bit. He did a thorough job and I am happy with the service call.
Great service and value
David - Pataskala, OH
Shane was our tech. He was thorough and honest. He explained it all to me (the wife) answering my questions. Plus the he didn’t try to sell me needless stuff. Because of the service Shane provided I will have Pickerington heat do my future air conditioner replacement work.
Kyle - Pataskala, OH
Scott Grady arrived on time and was very professional. He provided clear explanation of what he was doing during the diagnostic process and when explaining his findings.
Christine - Pataskala, OH
Laraine - Pataskala, OH
I have always had great service and this time was no different.
Great service - Answered my questions fully - Friendly
Dennis - Pataskala, OH
James - Pataskala, OH
Aaron - Pataskala, OH
Kevin - Pataskala, OH
I needed an estimate for storm damage and Pickerington Heating and Cooling was able to come out and give an estimate the same day
I completed a diagnostic on a Bryant A/C. I inspected the unit and found compressor fan not operational. Service disconnect has been bypassed - not to code. I found the dual capacitor is also not within spec. I replaced the compressor so I could further inspect unit. Contactor has burnt spots and pitting and charge is low. I recommend that due to the age, condition and cost of repairs (seen and unseen) that the unit be replaced. Provided replacement quote per customer request.
5250 Summit Rd SW Foote residence
I completed scheduled maintenance spring tune up on a Carrier heat pump. I visually inspected the furnace. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked voltage and amps. Inspected heat pump. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
I completed a repair on a Carrier A/C. I fixed 4 vents that weren't opening/staying open. I then checked charge which is where it should be. I cycled and monitored the system. Operating normally at this time.